Client Brief: Light (Lux) levels were not to be compromised in the Retail store when replacing Metal Halide and Halogen lamps with LED solution- > than 55% savings to be achieved in this Retail application. Specific connected load needed to be reduced to meet landlord’s specifications.
Store designed using LED, to achieve Energy cost savings as well as reduce heat load on air conditioning units of Shopping Mall. Single semi recessed LED Spots (20w) replace Metal Halide fittings (35w) and recessed single fitting-Halogen downlights (50w) replaced with MasterLED 6w GU10 LED down lights.
Mix of 4000k and 3000k Colour temperature used on light sources to enhance the CRI with a mix of Narrow and medium beam angles
Large energy savings: Instant >65% energy savings
Reduced Maintenance costs: the lamp life increases from 4000 hrs to 40 000hrs resulting in reduced disturbances to high traffic retail area.
Low heat production: Low heat emissions help to reduce air conditioning consumption
Specific connected load: Achieved <28w/m² specific connected load; beating landlords required shop fitting design specifications
CO² Emissions: Reduced CO² emissions by approximately 2.9 tonnes per year from this retail trading floor